The technician installed two outlets in the ceiling of the garage. He discovered that the ground fault breaker in the electrical box was not functioning. This was dangerous. He purchased a new breaker at my expense and installed it. Then checked to make sure the entire circuit was functioning properly.
- Approximate cost of services:
- Company Response
Thank you for review, it is much appreciated.